. Vertical floor type
: Technical spesefications
(H = 1320 mm), Air handling unit with humidification section, left, 4000 m3 / h
220 Pa, Qx = 29.6 kW, Qt = 54 kW, N = 1.1 kW, cassette filter, tnl = + 43.5 ° C, tvnl = 220C, X1 /
X2 = 7 / 120C, tnz = -140C, tvnz = 200C, T1 / T2 = 60 / 500C) Air conditioner control system: 1
valve, with continuously variable electric drive. Control cabinet. Control panel with display.
Temperature sensors. Air flow sensors. Starting and protective equipment.